I am looking for the MAX power consumption for a 6500-14
Hello Chad Buckland
About your question from the max power consumption on a 6500 14-slots. The following is from Technical Documentation 323-1851-151 Planning-Ordering Information located on the portal.
If a pair of stacked optical/rear electrical shelves are deployed, the following thermal engineering rules apply:
Note 1: The typical power consumption values are based on operation in a system operating at an ambient temperature of 25oC (+/-3oC) and voltage of 54 Vdc (+/-2.5 V) or in the full operational voltage range in the case of AC-powered equipment.Note 2: The power budget values are based on the maximum power consumption in a system operating at an ambient temperature range from 5oC to 40oC at a voltage of 40 Vdc (+/-2.5 V) or in the full operational voltage range in the case of AC-powered equipment. These values must be used in sizing feeders and estimating theoretical maximum power draw.Note 3: When equipped in a 14-slot packet-optical shelf (NTK503SA), half of this module's power (1W) is attributed to each of the two feeder zones.
If you need to check a existing shelf 6500 consumption power via Site Manager Go to Node Information-System and below has calculated shelf power (W).
Retrieving data ...